quality control technicianReport
Please briefly explain why you feel this question should be reported .
Just bought a house and during inspection everything was fine…I go to my garage and now the GFCI Is not lit. I take off the cover, pull the switch out, and I check the wires for current with my Klein voltage checker and the hot wire is live. …I’m assuming the switch is bad. Anyway, I also noticed that there are two wires going in and two wires going out. ..No ground! I did read on the Internet that this is still to code. …my question is…Should I make a piggy tail and ground the new switch to the metal Junction even though no ground is OK (if you want I can post the video with the code info)
in progress 0Electrical 6 years 1 Answer 990 views 0