30a 3-wire to 4-wire using a GFCI spa panelReport
Please briefly explain why you feel this question should be reported.
I am building a brewing control panel. I want to have GFCI so I don’t kill myself. So called Experts have posted the following on one of the brewing forums and I need to know if this is correct or not?
Thank you in advance!
Answer ( 1 )
Please briefly explain why you feel this answer should be reported.
First off. You’ll to come from a 50 to be able to go to a 50 amp. The panel will also need a ground. And what’s up with that jumper from the neutral to the ground?