Please briefly explain why you feel this question should be reported .
I want to add a 100 amp sub-panel from my main service panel.
The main service panel that is attached to the meter box has two hot lugs and one ground buss bar.
It does not have a neutral buss bar.
How do I connect a 2-2-2-4 wire (2 hots, a ground, and a neutral) to the three lugs in the main service panel?
I know that the 2 hot wires will connect to the hot screws of the 100 amp breaker and the ground (bare) wire will connect to the ground buss bar. Where do I connect the neutral wire since there is no neutral buss bar in the main service panel?
Please forgive the incorrect terminology. I’m still learning the basics of his stuff.
You have a great website.
in progress 0Electrical 5 years 2016-05-16T18:10:00-04:00 2016-05-16T18:10:00-04:00 3 Answers 695 views 0