Single pole 3 way switchReport
Please briefly explain why you feel this question should be reported .
I’m replacing a single pole 3 way switch. The existing switch is a lighted push on/off button switch which always stays lit. The new switch is an up & down (no light) switch. The wiring is black (common), white, red, and ground. I connected the black wire to the common area of the switch and the white and red to the travelers connections on the switch. Here’s what happens. When the switch is down (lights off) and the breaker is turned on, the breaker trips. If I have the switch up (the other direction) when the breaker is turned on, all the lights work properly. However, if I then flip the switch down to turn off the lights, the breaker trips again. We can’t figure why the breaker trips when the lights are in the off position.
in progress 0Electrical 5 years 1 Answer 660 views 0